Gas Furnace Maintenance
Are you looking for gas furnace maintenance in Springfield , PA ? Our heating and furnace service technicians have years of experience working on furnaces like yours in Springfield , PA. McGinley Services has service vehicles on call that are fully equipped with the tools and parts necessary to get your furnace back up and operating.
We offer gas furnace maintenance and maintenance agreements to keep your heating system running great. You can rely on McGinley Services to advise you properly and to do excellent work promptly. Ask us about maintenance agreements for your high efficiency furnace today.
We provide gas furnace Maintenance Agreements in Springfield , PA
Gas Furnace And Ac Tune Up 1 Year Old
All Pictures Attached
Cleaned Drain Lines Checked And Cleaned Flame Sensor
Ignitor Is Good Cleared Pressure Switch Tubing
Co Reading 9 Ppm
Joe , W. Springfield, PA
Heater Tune Up
Diana , W. Springfield, PA
Heater Tune Up
Hans , V. Springfield , PA
Replaced Gas Valve And Adjusted Gas Pressure To 3.5
Supply Temp 125 Return Temp 73
Tested Temperature At Daughter’s Bedroom Supply-113 And Also A Master Bedroom Supply-110
Gas Analysis Providing Good Results. Reads 20 PPM.
Thank You For Your Time And Business,
Brent And LorenOisin, B. Springfield, PA
Heater Tune Up For Maintenance Plan
Bill, G. Springfield , PA
Attic System 6yo Bryant 90% Furnace. System Over Heating. System Has .9 Static. Blower Over Amping. Filter Dirty. Gas Pressure At 3.5 Flame Sensor, Inducer Motor, And Blower Capacitor Test Within Range. Board Has Heat Damage. Electrical Connections Tight And Clean. System Running With 10PPM CO.
Jim , M. Springfield, PA
Tune Up On 24 Year Old Rheem Gas Furnace. Blower Wheel Dirty. Blower Motor, Blower Capacitor, And Inducer Motor Test Within Range. Filter Is In Good Condition. Flame Sensor Read Low, Removed And Cleaned Now Reads Within Range. Burners Have Intermittent Delayed Ignition. Gas Pressure Adjusted From 3.66 To 3.5. Flue Piping Has Some Rust Spots.
Advise Replacing Burners, Flue Piping And Cleaning Blower.
Due To Age And Cost Of Repair, System Replacement Is Recommended.
Client Opted To Replace Burners, Flue Piping, And Clean Blower Wheel.
Parts Ned To Be Ordered, Will Call When Parts Are In For Scheduling.
Kelsey, . Springfield , PA
Tune Up On 12 Yo Rudd 90 Furnace. Blower Wheel Has Some Dirt Accumulation.board Is In Good Condition, Free Of Any Damage. Electrical Connections Tight And Clean. Inducer Motor, Blower Motor, And Gas Pressure Test Within Range. Flame Sensor Tests Low, Removed And Cleaned, Now Reads Within Range. System Running With Elevated CO Levels Of 115PPM.
System Has Rust In Heat Exchanger.
Tested Humidifier, Humidifier Is In Working Condition.
Advise New Heat Exchanger And Blower Wheel Cleaning.
Due To Age And Cost Of Repairs, System Replacement Is Recommended.
Robert , D. Springfield , PA
Heat Tune Up On Gas Furnace.
Checked Filter, Not Due For Change
Checked Safety Loop, Ignition System Healthy
Tested Gas Valve Pressure, Within Range
Tested All Electrical, All With In Specifications
Flushed The Drain And Tested Condensate Pump
Combustion Results Within Range.
Kimberly, S. Springfield, PA